Membrane Type: Cross Linked Fully Aromatic Polyamide Composite
Construction: Spiral Wound Element
Application: Drinking Water
|Model||Diameter Inches||Salt Rejection %||Product Flow Rate gpd (l/h)|
|HM 1810-LPE-80||1.8||95%||80 (12.6)|
Feed Water Pressure: 75 psi (5.2 kg/cm2)
Feed Water Temperature: 77oF (25oC)
Feed Water Concentration: 500 ppm softened tap water
Recovery Rate: 15%
Feed Water pH: 6.5 – 7
Minimum salt rejection is 90%
Permeate flow may vary +/-20%
Maximum Operating Pressure: 150 psi (10.5 kg/cm2)
Maximum Operating Temperature: 104oF (40oC)
Maximum Cleaning Temperature: 104oF (40oC)
Feed Water Chlorine Concentration: Not Detectable
Feed Water pH Range, Continuous Operation: 2 – 11
Maximum Feed Water SDI (15 Minute Test): SDI < 5
Maximum Feed Turbidity: NTU < 1
- Follow instructions mentioned on the caution sticker placed on product packaging.
- The customer is fully responsible for the effects of chemicals that are incompatible with the elements.
- For element loading, use only the recommended silicon lubricant. The use of petroleum based lubricant or vegetable based oils may damage the element irreversibly.
- Membranes show some resistance to short-term attack by chlorine (Hypochlorite). Continuous exposure should be avoided as it may damage the membrane.